The technician was proactive in discovering & treating potential problems and also helpful in solving current problems. I have been with perfect service for over 10 years and have always received great service. thank you
CLEAN AND CHECK A/C. CHECK THERMOSTAT, CHECK AIR FILTER, CHECK ALL ELECTRICAL CONNECTIONS, CHECK CONDENSER COIL. CHECK FREON LEVELS, CHECK DRAINAGE. LUBRICATE ALL NECESSARY MOVING PARTS, ADJUST BLOWER COMPONENTS. EVERYTHING IS RUNNING GREAT.
CLEAN AND CHECK A/C. CHECK THERMOSTAT, CONDENSER COIL, CHECK AIR FILTER, CHECK AIR FLOW, CHECK ALL ELECTRICAL CONNECTIONS, CHECK DRAINAGE, CHECK FOR PROPER ENERGY CONSUMPTION. ADJUST BLOWER COMPONENTS, LUBRICATE ALL NECESSARY MOVING PARTS. EVERYTHING IS RUNNING GREAT.
Seasonal service work completed.
Service work performed for the Heil air conditioning unit with Heat pump cleaned air filter. Replaced valve core for UV light.
Customer satisfied with service work performed for the 2008 air conditioning unit with Zep con-coil cleaner.
Checked ducts for build on the 2011 air conditioning unit with heat pump. cleaned air filters, and checked freon pressure levels.
Cleaned and sanitized the Heil Air conditioning unit with Zep con-coil cleaner. No repairs needed.
Cleaning and servicing the Heil air conditioning unit with Zep con-coil solution.
Checked 2010 Heil heat pump with condensing unit for bad pressure switch, no other repair work needed.
No Repair needed on 2010 heat pump with condensing unit.
Service work done on 2015 heil air conditioner unit.
Birmingham Alabama Hvac service on a 6 year old Temp-Star and a 6 year old Heil unit. Check and clean coil condenser, adjust blower components making proper adjustments and cleanliness of blower and components are nessassary for adequate air flow.
Air Conditioning service. Diagnose, clean and performed annual AC maintenance and tune-up for service plan on Heil Cooling System. Cleaned condenser coil on outdoor air conditioner unit, check Freon pressures, cleared drain lines, oiled necessary moving parts, on 4 year old central HVAC system with R-410a. Heating and cooling maintenance complete which will help lower cooling cost for this residential customer. Cooling system is now ready for summer weather.
Technician came out on an annual service cleaning for the summer. Cleaned the outdoor unit, checked all the wiring, oiled moving parts, cleaned outdoor coil, also cleaned indoor evaporation coil. Checked all the inside equipment, duct work, thermostat. The customer is now ready for the summer months ahead.
CLEANED, TUNED UP, AND SAFETY CHECKED 6 YEAR OLD AC SYSTEM, INSTALLED UV, AND ALSO INSTALLED UV LIGHT.