Very respectful nice and friendly.
Seth was amazing! We will be requesting him for all of our needs!
System is working fine
The technician was professional and very thorough. His communication was excellent.
Technician was very thorough and professional.
Tech was prompt, professional and kept me informed.
Professional service at a fair price
Perfect Service replaced our AC/Heat unit quickly and professionally. Your guys were neat, leaving no mess and kept us advised of progress during installation.
Noah was VERY professional and thorough.
Our technician was on time, professional, and friendly. He did his job thoroughly, and repaired our HVAC system to working like new again. Thanks, Buddy! And kudos to Perfect Service Heating and Air.
Did an air conditioner repair on a 2yr old York unit in Mt Olive AL Checked the compressor
Did a heat repair on a 5yr old York system in Mt Olive AL Lubricated all moving parts
Did a heating repair on a 2yr old Trane unit in Mt Olive AL Checked all electrical connections
Did a heating repair on an 8yr old Ruud unit in Mt Olive AL Checked heat exchanger
Did a heat repair on a 2yr old Ruud unit in Birmingham AL Checked high limit control
Did a heating repair on a 7yr old Trane unit in Mt Olive AL Checked for cracks in the chamber
Did an AC maintenance tune-up in Mt Olive Al on a 5-year Lennox unit. Clean and check the condenser coil.
Did an AC maintenance check-up in Mt. Olive Al on a 1-year Heil unit. Clean and check the condenser coil.
Did an AC maintenance tune-up on 2 York units in Mt. Olive Al. Clean and check condenser coil.
Did an AC maintenance check-up in Mount Olive Al on a 4-year Trane unit. Check thermostat, air filter, and freon levels.
Did an AC maintenance tune-up in Birmingham Al on a 4-year Heil unit. Clean and check condenser coil.
Did an AC maintenance tune-up in Mt. Olive Al on a 2-year Heil unit. Check thermostat, air filter, and freon levels.
Came out to Mt Olive Al and did a maintenance check-up on a 10 Lennox unit. Check voltage and amperage on motors.
Came out to Birmingham Al and did an HT maintenance check-up on a 1 year Heil unit. Check all electrical connections.
Did an HT maintenance tune-up in Birmingham Al on 2 Carrier units, both 4 years. Clean and check burners and burner operation.