Knowledgeable, patient, extremely qualified, personable, overall great service with a lot of explanation
Noah did a great job. Very nice and respectful. You can tell Perfect Service Heating and Air preach that as a company. I will use no one else.
knowledgable professional personable complete with explanation not in hurry to leave without satisfaction guaranteed
I was very pleased with the service that I received on my heating and cooling system. The tech was very professional.
Taylor C. came and checked out my air conditioner in a very timely manner with very little personal contact. During this coronavirus time I really appreciate that. It checked out good for us. Thank you
Tech did a very good job. Very pleased.
Our technician was professional and stayed late to ensure our HVAC issues were addressed and repaired.
Good service - courteous
Did an HT maintenance tune-up in Odenville Al on a 9 year Goodman unit. Check heat exchanger, fan control, and adjust blower components.
Did an HT maintenance check-up in Odenville Al on 2 Carrier units, both 3 years old. Lubricate all necessary moving parts. a
Performed an a/c maintenance tune-up in Odenville Al on a 3 years Payne unit. Checked the capacitor, had to be replaced.
Did an a/c maintenance check-up on a 2 year Heil unit in Odenville Al. Check compressor delay safety controls.
Did an a/c maintenance check-up on a 7 year Payne unit in Odenville Al. Check voltage and amperage on motors.
Did an a/c maintenance check-up on 2 York units in Odenville, Al both is 1 year. Lubricate all necessary moving parts.
Did an a/c maintenance check-up in Odenville, Al on a 3 year Trane unit. Check thermostat, air filter, and airflow.
Did an a/c maintenance tune-up on 2 Lennox systems, both 8 years, in Odenville, Al. Check airflow, air filter, and thermostat.
Came to Odenville, AL, did a maintenance tune-up on a 2 year York system. Check all electrical connections.
Came out to Odenville, AL for an a/c maintenance tune-up on an 8 year American Standard system. Check thermostat, air filter, and airflow.
Did an a/c maintenance check-up on 2 Heil systems in Odenville, AL both 12 years. Check thermostat, air filter, and airflow.
A maintenance tun-up was done on a 7 year York a/c system in Odenville, AL. Check thermostat, air filter, and airflow.
Performed a maintenance tune-up in Odenville, AL on 2 Heil 11 years a/c systems. Replaced weak capacitor under warranty.
13 POINT MAINTENANCE TUNE-UP FOR 10 YR A/C UNIT. SLIGHT ISSUES WITH T-STAT. THE CUSTOMER CHOSE NOT TO ADDRESS THE ISSUE. ADVISED 1 YR FREE SERVICE AGREEMENT. CLEAN AND CHECK CONDENSER COIL, CHECK AIR FILTER, AIRFLOW, THERMOSTAT, FREON LEVELS, DRAINAGE, AND ALL ELECTRICAL CONNECTIONS. EVERYTHING IS RUNNING GOOD.
FIRST MAINT. CHECK-UP UNDER SERVICE AGREEMENT FOR 3 YR A/C UNIT, NO FURNACE SMELL. CHECK THERMOSTAT, AIRFLOW, AIR FILTER, FREON LEVELS, DRAINAGE, ENERGY CONSUMPTION, COMPRESSOR DELAY SAFETY CONTROLS, AND ALL ELECTRICAL CONNECTIONS. CLEAN AND CHECK CONDENSER COIL, CHECK VOLTAGE AND AMPERAGE ON MOTORS. LUBRICATE ALL NECESSARY MOVING PARTS AND ADJUST BLOWER COMPONENTS. EVERYTHING IS RUNNING GREAT.