The installation crew did a wonderful job. Their attention to detail was great!
HAD A SERVICE CALL, A/C. DRAINING EVERYWHERE, CHECK DRAINAGE. REDID DRAIN. CHECK VOLTAGE AND AMPERAGE ON MOTORS. CHECK CONDENSER COILS. CHECK AIR FLOW. EVERYTHING IS RUNNING GREAT.
HAD A SERVICE CALL. CAME OUT AND INSTALLED A 3T XX PK. MADE SURE THE UNIT WAS INSTALLED PROPERLY. CLEANED UP THE WORK AREA WHEN LEFT. CHECK AIR FLOW, ALSO THE GAS. EVERYTHING WAS WORKING GREAT.
CLEAN AND CHECK A/C. CHECK CONDENSOR COIL, ADJUST BLOWER COMPONENTS, LUBRICATE ALL NECESSARY MOVING PARTS, CHECK AIR FLOW AND ALL ELECTRICAL CONNECTIONS. EVERYTHING RUNNING GREAT.
Clean & Check 3yrs A/C unit. cleaned condenser coils, check blower, lubricated all moving parts that saw necessary, etc. Everything running great.
Checked ducts for build up, cleaned condensation drain, no repairs needed.
Service work completed for the Heil 2014 air condensing unit with Zep con-coil cleaner.
Cleaned and safety checked the 2014 Heil air conditioning unit with Zep con-coil cleaner. No repairs needed.
Cleaned and serviced 2010 heil heat pump condensing unit.
Clean and check on 2010 air conditioning unit sone.
Quinton Alabama customer with winter heat maintenance on a 6-year-old Trane. Check the burner Assembly to remove any rust dust and debris off the burners so gas can flow properly and efficiently.
Buddy did the air conditioning service. Diagnose, clean and performed annual AC maintenance and tune-up for service plan on Heil Cooling System. Cleaned condenser coil on outdoor air conditioner unit, check Freon pressures, cleared drain lines, oiled necessary moving parts, on 1 year old central HVAC system with R-410a. Heating and cooling maintenance complete which will help lower cooling cost for this residential customer. Cooling system is now ready for the summer.
CLEANED AND TUNED UP 5 YEAR OLD HEATING SYSTEM.
TUNEUP & MAINTENANCE ON CENTRAL HEATING SYSTEM FOR FALL/WINTER.