From the beginning phone call, service was outstanding and extremely helpful, me and my family were in dire straits, as our two year old unit was not functioning properly, a technician was dispatched on time as stated from the earlier phone call, the technician also called upon arrival and quickly assessed the issue, and worked diligently to correct the issue, he fought mosquitos, the dark and the heat so that me and my family could enjoy a nice cool home, he never complained or missed a beat, fantastic personality and an excellent work ethic, truly an amazing experience for me and my family compared to the last company that actually installed the unit, i should have used perfect service company the first time, and all would have been well as it is now, thank you so much for your kind knowledgeable staff, and technicians that really know how to handle problems and are trained properly to complete repairs in one visit, a true joy to experience.
The installation crew did a wonderful job. Their attention to detail was great!
CLEAN AND CHECK HT. CHECK THERMOSTAT, CHECK HEAT EXCHANGER, CHECK HIGH LIMIT CONTROL, CHECK BURNERS AND BURNER OPERATION, CHECK AIR FILTER, CHECK GAS PRESSURE AND FOR PROPER VENTING, CHECK ALL ELECTRICAL CONNECTIONS, CHECK HUMIDIFIER. ADJUST BLOWER COMPONENTS, LUBRICATE ALL NECESSARY MOVING PRART. EVERYTHING IS RUNNING GREAT.
CAME OUT ON A ESTIMATE FOR ADC. INSTALLED A PREM ADC. MADE SURE EQUIPMENT WAS INSTALLED PROPERLY. CHECK THERMOSTAT, CHECK AIR FILTER, CHECK ALL ELECTRICAL CONNECTIONS, CHECK FOR CORRECT AIR FLOW IN HOME. EVERYTHING IS RUNNING GREAT. NEW SERVICE AGREEMENT.
CAME OUT ON A SERVICE CALL, A/C. CHECK THERMOSTAT, CHECK CONDENSER COIL, CHECK DRAINAGE. FOUND CLOGGED COIL, DID COIL CLEANING. CHECK COMPRESSOR DELAY SAFETY CONTROLS. EVERYTHING IS RUNNING GREAT.
CAME OUT ON A ESTIMATE. PURCHASED 2.5T XX EVAP. MADE SURE SYSTEM WAS INSTALLED PROPERLY, MADE SURE WORK AREA WAS CLEAN WHEN FINISH. CHECK THERMOSTAT, CHECK ALL ELECTRICAL CONNECTIONS, CHECK AIR FILTER. EVERYTHING IS RUNNING GREAT.
CLEAN AND CHECK A/C. CHECK THERMOSTAT. CHECK FREON LEVELS, CHECK CONDENSER COIL. CHECK DRAINAGE. HAD TO RUN A NEW DRAINLINE. CHECK ALL ELECTRICAL CONNECTIONS. LUBRICATE ALL NECESSARY MOVING PARTS, ADJUST BLOWER COMPONENTS. EVERYTHING IS RUNNING GREAT.
HAD A SERVICE CALL, A/C. DRAINING EVERYWHERE, CHECK DRAINAGE. REDID DRAIN. CHECK VOLTAGE AND AMPERAGE ON MOTORS. CHECK CONDENSER COILS. CHECK AIR FLOW. EVERYTHING IS RUNNING GREAT.
HAD A SERVICE CALL. CAME OUT AND INSTALLED A 3T XX PK. MADE SURE THE UNIT WAS INSTALLED PROPERLY. CLEANED UP THE WORK AREA WHEN LEFT. CHECK AIR FLOW, ALSO THE GAS. EVERYTHING WAS WORKING GREAT.
CLEAN AND CHECK A/C. CHECK CONDENSOR COIL, ADJUST BLOWER COMPONENTS, LUBRICATE ALL NECESSARY MOVING PARTS, CHECK AIR FLOW AND ALL ELECTRICAL CONNECTIONS. EVERYTHING RUNNING GREAT.
Clean & Check 3yrs A/C unit. cleaned condenser coils, check blower, lubricated all moving parts that saw necessary, etc. Everything running great.
Checked ducts for build up, cleaned condensation drain, no repairs needed.
Service work completed for the Heil 2014 air condensing unit with Zep con-coil cleaner.
Cleaned and safety checked the 2014 Heil air conditioning unit with Zep con-coil cleaner. No repairs needed.
Cleaned and serviced 2010 heil heat pump condensing unit.
Clean and check on 2010 air conditioning unit sone.
Quinton Alabama customer with winter heat maintenance on a 6-year-old Trane. Check the burner Assembly to remove any rust dust and debris off the burners so gas can flow properly and efficiently.