They were very professional they just came to do a regular service but found black mold spores growing inside of my unit. Talked to me about the action that needed to take place to remove all of the mold so it would be completely gone.. I have breathing issues already COPD & Asthma this was a no brained for me it had to be done ASAP they made arrangements for that same day. I was very satisfied with the service and all of the employees were professional. The total experience was great. I have told lots of other people about my experience. They always installed a dehumidifier for me that day . It’s amazing how much better the air quality is in my house.
The tech was very helpful and super nice !
CAME OUT ON AN ESTIMATE FOR EQUIPMENT. INSTALLED 4T HP AND AH, MOBILE HOME UNIT. 7Y P&L. SYSTEM WAS INSTALLED CORRECTLY AND WORK AREA WAS CLEAN WHEN FINISH. CHECK THERMOSTAT, ENERGY CONSUMPTION, CONDER COIL, COMPRESSOR DELAY SAFETY CONTROLS, AIRFLOW, AIR FILTER, AND ALL ELECTRICAL CONNECTIONS. EVERYTHING IS OPERATING GOOD.
2ND MAINTENANCE TUNE-UP UNDER SERVICE AGREEMENT FOR 7 YR A/C UNIT. RENEWED SERVICE AGREEMENT. LUBRICATE ALL NECESSARY MOVING PARTS, AND ADJUST BLOWER COMPONENTS. CLEAN AND CHECK CONDENSER COIL. CHECK VOLTAGE AND AMPERAGE ON MOTORS. CHECK THERMOSTAT, AIR FILTER, AIRFLOW, FREON LEVELS, DRAINAGE, ENERGY CONSUMPTION, AND ALL ELECTRICAL CONNECTIONS. EVERYTHING IS GOOD.
CAME OUT ON A SERVICE CALL A/C. WAS HAVING DRAINAGE PROBLEM. INSTALLED A 3.5T XX A/H COND PUMP. MADE SURE SYSTEM WAS INSTALLED PROPERLY. CHECK ALL ELECTRICAL CONNECTIONS, CONDENSER COIL, CHECK THERMOSTAT. CHECK DRAINAGE. EVERYTHING IS RUNNING GREAT.
CLEAN AND CHECK A/C. CHECK AIR FLOW CHECK ALL ELECTRICAL CONNECTIONS, CHECK CONDENSER COILS. MADE SURE SYSTEM WAS INSTALLED PROPERLY. MADE SURE WORK AREA WAS CLEAN WHEN LEFT. CHECK AIR FLOW AFTER INSTALLATION. EVERYTHING IS RUNNING GREAT.
INSTALLED AIR DUCT CLEANING PREM ADC. MADE SURE EQUIPMENT WAS INSTALLED PROPERLY. MADE SURE DUCTS WAS CLEAN, CHECK AIR FLOW. MADE SURE WORK AREAS WAS CLEAN WHEN LEFT. EVERYTHING IS WORKING GOOD.
Service work completed for 2010 air condensing unit with heat pump. checked ducts for build up, no repairs needed.
Service check completed, checked filters and operating freon levels. Maintenance work completed. No repairs needed.
Checked all moving parts, cleaned air filters, and adjusted blower motors. best heating and air company in 35131.
Cleaned condensing unit, checked manifold pressure, cleaned condensing drain.
Cleaned and sanitized the Heil 2009 air conditioning unit with heat pump, No repairs needed. Checked burners for build up.
Serviced and sanitized the 2011 Heil Air conditioning unit with Zep con-coil cleaner. No repairs needed.
We did the summer cleaning for this customer. We also did a safety inspection on his heat for the fall & winter. Air conditioner looks great!