CLEAN AND CHECK A/C. CHECK CONDENSER COIL, CHECK CONDENSATE DRAIN FOR DRAINAGE. HAD TO REPLACE CONDO. PUMP. CHECK COMPRESSOR DELAY SAFETY CONTROLS, CHECK AIR FLOW. EVERYTHING IS RUNNING GREAT.
Checked ducts for build up, cleaned condensation drain, cleaned air filter.Replaced UV light.
Service work performed for 2014 heil heating and air conditioning unit with heat pump. cleaned condensation drain and condensing coil with Zep con-coil cleaner.
Installed the new 2017 Heil air conditioning unit with heat pump. 12yr warranty on parts and labor
Cleaned and sanitized the Heil Air conditioning unit with heat pump.
Riverside Alabama customer clean and check on 3-year-old Ruud. Check thermostat to make sure the thermostat is turning on and off at the proper temperature.
CLEANED AND TUNED UP 3 YEAR OLD AC SYSTEM FOR SPRING AND SUMMER.
DID THE SUMMER MAINTENANCE ON 2 YEAR OLD AC SYSTEM.