Diagnostic Performed Replaced OEM Secondary Circuit Board On Armstrong Gas Furnace To Keep Furnace Running Efficiently For The Winter Season
Diagnostic service performed on a Rheem furnace. Secured drain line with metal plumbing strap, cleared out trap to the furnace. Confirmed the blower motor is going bad. Quote provided to replace the motor.
Free quote provided to install a Carrier "Infinity Series" 18 SEER Variable-Speed 3 Ton Heat Pump. 60 months 0% interest offered through Wells Fargo and a one year service maintenance agreement .
Diagnostic Service Call on ARMSTRONG unit. Customer stated furnace was not heating. Found furnace tripped out on high limit switch. Furnace filter is good. Found blower motor not spinning. Tested capacitor. 4.9/5 (Good). Wheel is stiff and hard to turn, does not free spin. Blower motor is going bad. Customer was not home at time of appointment. Left voicemail waiting for a call back
Replace Out of Warranty Part on Comformaker- Installed new 40mfd capacitor on blower motor. Cycled system everything operating correctly.
Checkout / Tune-Up-Recommend new humidifier pad