Thermal Zone furnace was not heating. Found furnace locked out on fault code upon arrival. The drain was clogged. Cleaned the drain and now the system is operating properly.
Technician diagnosed a Honeywell humidifier that was not operating properly. He found that it was not set high to run. All is functioning at this time.
Technician diagnosed a faulty ignitor on a Trane furnace. The ignitor was resisting the flow of current. The customer was given a quote for repair and for a replacement of the system. The customer opted to purchase a new furnace.
Performed Our Special Tune-Up & Safety Checkout On Carrier Gas Furnace To Keep Furnace Running Efficiently For The Fall/Winter Season