Diagnostic Performed Gas Valve Issues On Janitrol Gas Furnace Recommended Customer Contacting Gas Company To Turn On Gas To Further Diagnose Issues
Diagnostic Service Call for 2005 Carrier Heat Pump, Tech found imploded capacitor with burnt wire, Tech replaced with new 50/5 and secured wire.
Performed Pre-Season Tune-Up & Safety Checkout On Lennox Gas Furnace To Keep Furnace Running Efficiently For The Winter Season
Installing New Carrier "Infinity Series" 96% Variable Speed Two-Stage 80,000 BTU Gas Furnace & New Carrier 14 SEER 3 Ton Heat Pump To Replace Existing Rheem AC & Furnace
Replaced Dual Capacitor On Goodman AC System To Help Keep AC System Running At Highest Performance For The Summer Season
Trane furnace repair