Always on time,courteous,and knowledgeable.They are the only hvac company we use.
We have had a maintenance or service plan with Pickerington heating and cooling for a number of years and at two homes. We have always been very very happy with all of their work. Recently we have a new heating and cooling system installed. The price was awesome and the installers were pleasant and professional. All around a pleasure to have in our home! The new system is fantastic, we are very pleased. We also had all of our duct work cleaned and that crew was very nice too, they even happily moved furniture and were very careful!
We have been with this company for about 8 years and they just get better and better, and they were great to start with. We renew a service agreement every year and when we need them they come that day. There are lots of perks that save you money with the service. Now we have having them install a new furnace and air and the price was unbelievable and within our budget. We have no doubt we will be completely satisfied, they always make everything right!
Used this company for years & have yearly maintenance agreements. In any emergency they come immediately!
I called on a Saturday morning,and the tech was here that afternoon.He was courteous,knowledgeable,and had my central air running in 20 minutes.Noah was great.
Diagnostic Service Call on TRANE furnace/ Blew out drain line, tested draft with exhaust on and off, fail draft. Did combustion test, combustion test fail. Bad head exchanging. Quoted 1400 for warranty heat exchanger. Customer wants refunded for pressure switch.
Replaced out of warranty part on GOODMAN furnace/ Replace OEM Main Circuit Board/ Replace OEM Flame Sensor
Diagnostic Service Call on 2015 Goodman. Replaced faulty flame sensor.
Furnace Tune Up & Safety Inspection on 2018 Carrier unit.
Spring Season AC Tune-up and Safety checkout performed over a 2018 Carrier "Infinity Series" 18 SEER Variable-Speed 4 Ton Heat Pump. System is up and ready to go for the summer season.
Upon inspection of a TRANE AC System, found the capacitor at 0/5 and 0/35. Replaced at customer request the Dual Capacitor 35+5. System fully operational at this time.
Goodman AC not blowing cold air. Capacitor needs replaced and unit low on refrigerant. Replaced the Dual Capacitor 55+5 and recharged system with 2 lbs of R-22 Freon and added Easy Seal. System is functioning at this time.
Replaced Defrost Board System
Maintenance on ac unit - tuneup / checkout
61190 PHC - PRE (Checkout / Tune-Up)
Ac tune up Alexandria
Pre-season tune up performed on infinity AC unit near Alexandria Ohio