The technician was very cordial and efficiently performed the work needed. He was very knowledgeable and provided honest recommendations, with no high-pressure sales, and all for the right price.
My experience was great. Tech was very professional, courteous and knowledgeable. I was very satisfied with his work and the short time it took him to diagnose and fix the problem with my A.C. I will definitely continue using PIckerington Heating and Cooling for all my future needs
Thank you for prompt service and repair in our Air conditioner.
Great Service for a good price!
I have been using Pickerington Heating and Cooling for several years and have always had excellent service. All the guys are pleasant and very attentive to my service and always have a smile on their face. Love having this company that I can count on!
The service is quick and received a good quote
I have used Pickerington H&AC for 3 years. Expert and honest techs are keeping my unit running as intended. I will continue to use them.
Had great service. The technician was running late but I was kept updated and asked if it was okay to still come or reschedule. I was just happy I called that day and they made it a priority to come as soon as possible.
The tech explained the options and pricing. After discussing the option for a good price on a new unit.
Performed a thorough checkout of a 96% Carrier "Infinity Series" gas furnace. All components are running at manufacturer's recommendations. The system is ready for the winter season.
Technician installed an Aprilaire 600M humidifier to accompany a Bryant furnace. Both units are operating properly and efficiently.
Performed complete tuneup and safety inspection on a Carrier furnace to ensure efficient operation for the winter season of 2019/2020.
Technician diagnosed a Concord furnace that was intermittently operating when called to heat. Customer stated that basement had flooded the previous summer. The technician found that the filter was damp and dirty and had been sucked into the motor somewhat. He removed the filter and inspected the system. It is now operating properly.
Diagnostic service performed found furnace has a bad board.
When the technician arrived the Gas Lennox Furnace was not operational. After running a diagnostic the findings revealed a broken threading and the technician reinsert the fitting to get the unit to fire up and now the heat is functional once again. Technician did suggest a replacement unit.
Diagnostic Performed Replaced Inducer Motor & Circuit Board On Comfortmaker Gas Furnace To Keep Furnace Running Efficiently For The Winter Season
Diagnostic Performed Installed Inducer Motor & Switch On Comfortmaker Gas Furnace To Keep Furnace Running Efficiently For The Winter Season
Pre season tune up/check out on a CARRIER brand furnace.
Semi annual (FALL) Scheduled Maintenance on LENNOX furnace.
Diagnostic Performed Re-Set Breaker On Carrier Gas Furnace To Keep Furnace Running Efficiently For The Winter Season