All reps I met were friendly, courteous and customer oriented
Furnace tune - up and safety check performed on a Carrier Gas Furnace unit. Confirmed that the system is working within manufacturer specifications. Pictured is the customer's Carrier Gas Furnace.
Furnace Tune p & Inspection On 2018 Carrier Furnace
Diagnostic Service Call on Bryant furnace. Tech cleared debris from intake.
Upon inspection of 2017 Carrier furnace, found the blower door was ajar. Realigned both blower and burner doors to close door switch. Furnace is clean and fully operational at this time.
Diagnostic service Call on 2012 Comfortmaker
Technician performed Minor rewiring repair made on customer's thermostat. Removed the common wire from a battery only thermostat. System is operating properly in heating and cooling.
Furnace tune - up and safety check performed on a Comfortmaker system. Confirmed that the system is working within manufacturer specifications.
Furnace Tune Up on 2018 Carrier unit.
Diagnostic Performed Installed Offset Coil Adapter On Carrier AC System TO Keep AC Running Efficiently For The Summer Season
Tune up & Safety check performed on a Carrier Gas furnace & Carrier AC unit.