All reps I met were friendly, courteous and customer oriented
Free in-house estimate provided to replace a Trane Air Conditioner with a Carrier 16 SEER A/C System. Rebate given for AEP customer.
Performed check out- inspection of Nordyne A/C unit.
Performed safety check and tune- up on Nordyne A/C unit.
Performed service cal on LENNOX A/C unit. Checked volts, Confirmed none going to unit. Corrected issue
Customer stated 2018 Carrier unit is not cooling properly. Tech added small amount of r-410, cleaned coil and filter unit cooling at time of departure.
Replaced blow motor on Lennox A/C unit. Went over estimate for new Carrier system with owners.
Diagnostics service appointment for a 2014 Goodman Air Conditioner.
Performed check out of Trane A/C unit.
Upon inspection of Lennox unit, found issue with blower motor. Discussed options with customer. Repaired for now and provided estimate on new unto.
performed leak check on American standard a/c unit.
Unit had a blown capacitor. Replaced capacitor, system working within specs.
Carrier AC just received a preseason tuneup. Everything looks good currently. Amps draws, and temps all look good. The capacitor was low. The customer opted to replace it. The unit is working properly upon departure.
Estimate provided to replace a Goodman Air Conditioner with a Carrier 13 SEER 2 Ton Air Conditioner. One year service maintenance agreement included.