Great service quick and on time
Technician was awesome. Knowledgeable, helpful. Did an excellent job.
Diagnostic services found wires clipped to reversing valve were found to be loose. Tightened wiring and installed WiFi capable thermostat at customer request.
No cool air blowing from GOODMAN unit. Performed service call and cleaned coils, checked capacitor and replaced at customer request.
Tune-up and safety checkout performed on a 1998 Bryant Gas Furnace for a customer selling their home. Replaced the Capacitor 3.
Estimate for Replacement of HVAC system
Diagnostic of a Duncan AC unit. Charged unit with 2 lbs of R-22 Freon.
JOHNSTOWN A/C DIAGNOSTIC
Working on TRANE air conditioner and furnace
Johnstown a/c estimate
Tune-Up On Ducane AC