Great service quick and on time
Technician was awesome. Knowledgeable, helpful. Did an excellent job.
Replaced out of warranty part on BRYANT furnace. Replaced gas valve and cleaned flame sensor. Bubble tested joints. All ok.
Technician diagnosed Comfortmaker furnace with a faulty circuit board. He replaced it with an OEM board and now the furnace is operating properly and efficiently.
Technician came to customer's home to Program a Nest thermostat for a duel fuel heating system. Confirmed proper operation upon departure.
Diagnostic services found wires clipped to reversing valve were found to be loose. Tightened wiring and installed WiFi capable thermostat at customer request.
No cool air blowing from GOODMAN unit. Performed service call and cleaned coils, checked capacitor and replaced at customer request.
Tune-up and safety checkout performed on a 1998 Bryant Gas Furnace for a customer selling their home. Replaced the Capacitor 3.
Estimate for Replacement of HVAC system
Diagnostic of a Duncan AC unit. Charged unit with 2 lbs of R-22 Freon.
JOHNSTOWN A/C DIAGNOSTIC