The technician was professional and courteous as he was looking over my a/c unit. He was also knowledgeable with the current issue and what to expect in the future.
Great people and great price. Easy people to talk too.
The employee was very kind and acted in a professional manner
Paid 650 to fix AC worked for 2 days only. Called them back and they said needed another 700 dollars of work. I was not happy at all and have decided to go elsewhere
Diagnostic service call on 1990 York AC unit
Diagnostic Service Call on Trane unit
Replaced blower motor on 2008 Goodman unit.
Diagnostic Service Call for 2008 Goodman unit to replace blower motor
Furnace Tune Up & Inspection for 2019 Carrier unit.
Pre-Season Special Tune-Up and Safety Check performed on Carrier Gas Furnace. All levels found to be within manufacture specifications.
Special Pre-Season Fall Furnace Tune-Up and Safety Check performed on a 2005 Comfortmaker Unit.
Tune-up & Safety check performed on a Gas Comfortmaker Furnace unit.
Diagnostic Service Call on Trane unit, low on refrigerant, added R-22
Diagnostic Service Call on AC unit, added R-22 Freon and provided estimate on new system.
duct cleaning and gas furnace tune up
Furnace Tune up & Safety check out performed on a Goodman AC Unit