Everything went well. Very knowledgeable technician who shared some good tips and was very patient in answering questions! Very satisfied with the service!!
Appreciate the same day service. Technician Mike was very professional.
The repair technician was very polite and on time. Put dust cover on shoes which I appreciate
We are very pleased we chose Pickerington Heating & Cooling. They are always helpful in scheduling and their technicians are courteous, friendly and knowledgeable. We decided to purchase a contract with Pickerington Heating & Cooling to make sure we are covered for any issues that may arise. Would totally recommend them for your heating and cooling needs.
Ben Johnson is a plus for the image of your company going forward.
Have used before and always satisfied.
My overall experience has been excellent with Pickerington Heating and Cooling. Very professional and courteous. They arrived on time and were very friendly and knowledgeable. The two took the time to also explain every question that I had and offer very great advice.
James fixes my issue quickly thanks James!
I am very pleased with the service from Pickerington Heating and Cooling. I highly recommend.
Checked gas leak.
Diagnostic service call 2007 AC unit.
Furnace tune - up and safety check performed on a Carrier system. Confirmed that the system is working within manufacturer specifications.
Replaced a blower motor on a Trane system.
Removed and replacing removed thermostat wires for outdoor system. Dual capacitor on a unit.
Provided Estimate New Carrier Gas Furnace 96% Variable Speed Two-Stage 100,000 BTU To Replace Existing Lennox Gas Furnace
Performed Our Special Tune-Up & Safety Checkout On Rheem Gas Furnace To Keep Furnace Running Efficiently For The Fall/Winter Season
Diagnostic Performed Replaced Dual Capacitor On AC System To Keep AC Running At Highest Performance For The Summer Season
Installed New Carrier 80% 70,000 BTU Gas Furnace & New Carrier 13 SEER 2.5 Ton Air Conditioner To Replace Existing Carrier AC & Gas Furnace
Checked unit found both filters plugged removed maint going to replace
Dual Capacitor 45+5 replaced on 2012 Trane Air Conditioning System. System cooling as expected upon technician departure.
Diagnostic Performed Added Puron To Trane AC System To Keep AC Running At Highest Performance For The Summer Season
Diagnostic Performed Replaced Dual Capacitor On Bryant AC System To Keep AC Running At Highest Performance For The Summer Season
Performed Our Special Tune-Up & Safety Checkout & Added Freon To Bryant AC System To Keep AC Running Efficiently For The Summer Season
Diagnostic Performed Replaced Communicating Dampers On Bryant AC System To Keep AC Running Efficiently For The Summer Season