we put in a Carrier 80% Gas Furnace, and Carrier 13 SEER 2 Ton Air Conditioner that are running great!
Tech gave customer estimate for a new Carrier ac and furnace
Performed tune up on Carrier A/C unit.
Gave AC quote to replace equipment
Spring Season tune-up and safety checkout performed on a Carrier 13 SEER 2.5 Ton Air Conditioner as part of a service maintenance agreement.
Upon inspection of a Carrier 13 SEER 1.5 Ton Air Conditioner found system at 143/260 with 11 degree sub-cool out of 14 and 15 degrees suer heat. Also found blower speed set too high, set to correct 800cfm setting. Sub-cool outside is 8 degrees now, added refrigerant R-410A to system to bring pressures up to normal. Will come out tomorrow to finish recharging the system.
Condensor fan motor replacement
COLUMBUS A/C SERVICE
Columbus a/c service