Furnace tune - up and safety check performed on a furnace unit. Confirmed that the system is working within manufacturer specifications
Diagnostic Service Call on TRANE furnace. ran system with no faults. Tested flame sensor reading 1.5uA cleaned it now reading 2.1uA which is still to low. recommended replacing flame sensor or waiting to see if the furnace is having an intermittent issue. clean filter
Replaced in warranty part on Armstrong Model furnace. Arrived on site replaced inducer motor. System worked over night for customer. Replaced inducer motor with new style motor. Cycled on 2-3 times to ensure proper function and system functions perfectly fine at this time. System fully operational.
Technician diagnosed faulty inducer motor on an Armstrong furnace. He replaced the inducer motor and now the system is operating properly and efficiently.
Diagnostic Performed Replaced Ignitor On Trane Gas Furnace To Keep Furnace Running Efficiently For The Winter Season
we put in a Carrier 80% Gas Furnace, and Carrier 13 SEER 2 Ton Air Conditioner that are running great!
Tech gave customer estimate for a new Carrier ac and furnace
Performed tune up on Carrier A/C unit.
Gave AC quote to replace equipment
Spring Season tune-up and safety checkout performed on a Carrier 13 SEER 2.5 Ton Air Conditioner as part of a service maintenance agreement.
Upon inspection of a Carrier 13 SEER 1.5 Ton Air Conditioner found system at 143/260 with 11 degree sub-cool out of 14 and 15 degrees suer heat. Also found blower speed set too high, set to correct 800cfm setting. Sub-cool outside is 8 degrees now, added refrigerant R-410A to system to bring pressures up to normal. Will come out tomorrow to finish recharging the system.