When the temperatures dropped recently, I realized our heat had stopped working. Pickerington H&C had been out earlier in the year for a furnace tune-up so I scheduled an appt online on Saturday afternoon. Monday morning, a tech came and diagnosed a bad circuit board in the furnace. Later that afternoon, another tech came to install the board and get the heat working again. Family happy!
Upon inspection of a 2005 Bryant cooling system, found the capacitor visually ruptured. Replaced Dual Capacitor 45+5 and system came on with no issues.
AC diagnositic and repair
Estimate for full system!
61297 PHC - PRE (Checkout / Tune-Up)
Ac and furnace tune up
Working on Trane ac
SERVICE CALL - GAS UNIT
Duct cleaning, humidifier install and Bryant furnace tune up
Carrier furnace tune up
Plain City OH, furnace checkup.
Aprilaire humidifier clog
Aprilaire 600 install
Bryant furnace tune up
Bryant system check out for rattle noise