Matt was very knowledgeable Technician and explained everything as he was checking the A/C unit. He was able to track down the problem and made a number of calls to understand my options for correcting. Matt seemed sincere in helping make it the best experience he could. Overall it was a very good experience.
The furnace was not working. Matt traced the electric power thru the system and documented where it Failed and quoted me on the repair. I am deciding wetner to replace the furnace or repair it.
The check of the AC unit went fine. It appeared to be thorough and was done on time and as expected. My only problems were the thermostat was not turned back on to heat (it’s a cold Spring) and the door to the furnace room was left open.
Carl arrived on time, explained the service to be performed and was very helpful with thermostat programming. Carl also informed me of service results.
Great and prompt service, and very friendly!
I called on a Friday for non-emergency service and had an appointment for Monday. I know at some point I will probably need to replace my old furnace, but until then, I will trust Pick Heating & Cooling to take care of it.
Diagnostic Service Call on OIL Furnace. Checked unit found has water in system. Pumped 5 gallons of water out of line/tank. Put in new oil filter. Unit is running but needs barometric damper, oil nozzle .65 70B and filter 1A30 changed. Will quote.Pump water from system 5 gallons, change oil filter and cleanup nozzle and electrode. System start up
Follow up service on Carrier - Customer stated furnace would not ignite. Working at thermostat is correct. Getting correct voltage to system. Ignitor turns on but no gas. Found gas valve turned off from install. Turned gas valve on and system came right on. Temp rise of 48.
Performed Our Special Tune-Up & Safety Checkout On Bryant Gas Furnace To Keep Furnace Running Efficiently For The Fall/Winter Season
Semi annual scheduled maintenance on BRYANT A/C unit.
Free second diagnostic opinion of a 2002 Carrier Air Conditioner. Confirmed system has major leak and recommended to replace the system.
Completed a Scheduled Maintenance Tune-up on a Bryant Air Conditioner. AC is primed and ready to beat the heat.
AC tuneup done on an Armstrong AC unit. I found that the unit needed half of pound of R-22.