Diagnostic service call on LENNOX A/C unit. Upon arrival found that customer had changed capacitor on his own and had it working. fired up AC and went around side of the house to white smoke surrounding unit. Pulled disconnect and observed freon shooting from compressor. After removing top, checked capacitor and found it was wired incorrectly according to schematics. purple on common, red on herm, yellow on fan needed to be...purple to fan, yellow to herm, red to common after re wiring, tried to start back up and observed compressor fan popping and sparking. Shut unit off and spoke to customer about repair vs replace. customer going with new unit.
Installed PVC Trap with minor repair on Bryant cooling system to allow the condensate to properly drain.
Working on TRANE air conditioner and furnace
Sunbury humidifier install
Trane air conditioning repair
Quote on new system