Absolutely positively outstanding very punctual very professional very courteous got job done in a timely manner couldn't ask for anything better
Furnace Tune Up & Safety Inspection on 2011 Gas Comfortmaker Furnace.
Installed NEST thermostat. The system is operating properly.
Thermostat was programmed incorrectly by not being set up for a heat pump. Reset thermostat appropriately. Now the furnace is operating properly.
Performed fall tuneup on Comfortmaker furnace. The system is operating properly and is within manufacturer's specifications. It is ready to heat this winter season.
Customer wanted estimate on new system to replace current Goodman furnace. Pictured below is the Goodman.
Technician replaced the wet stitch on a Carrier furnace to ensure proper draining. The furnace is operating properly and efficiently and is ready for the winter season.
Replaced a part on Goodman furnace for the customer, to ensure a warm home during the winter months. Pictured is the customer's Goodman Furnace.
Diagnostic Service Call on Goodman furnace. Customer says the unit does not stay lit for longer than 5 seconds. Started unit at thermostat, furnace stays on. Pulled flame sensor, visibly dirty. Removed and cleaned.
Diagnostic Service Call on RHEEM furnace. Unit needs blower motor and wheel. Owner wants to replace
Semi annual (FALL) Scheduled Maintenance on residential furnace.
Tech replaced Humidifier Pad
Furnace Tune Up & Inspection on Rheem furnace.
Furnace Tune Up on 2017 Carrier Unit.
Pre season tune up/check out on Carrier on TRANE furnace. an the tune-up. Blower capacitor was found to be low, replaced at customers request. All levels were within specifications. Upon departure, unit is operating as expected.