Absolutely positively outstanding very punctual very professional very courteous got job done in a timely manner couldn't ask for anything better
Furnace Tune Up on 2017 Carrier Unit.
Outdoor capacitor reading 0 rated 30/5 and system blew a fuse. Dual Capacitor and plug-in fuse replaced and system is fully operational upon departure.
Summer Season A/C Tune-up and Safety Check performed on a 2018 Bryant System. System is running great and ready for the summer heat.
Tune up and Safety check performed on a Carrier AC Unit.
Minor wiring repair completed on 2003 Lennox Air Conditioner. System operating within manufacture specifications at this time but recommended general maintenance.
Ac tuneup done on an American Standard AC. It was determined there was a leak and customer opted for a new system rather than repair.
Performed an annual Tune-up on a Trane AC system. AC is cooling as it should.
AC Tune-up on 2017 Carrier brand AC unit. Checked furnace. Changed blower capacitor with 5 mfd. Changed filter.Checked AC. Capacitor was fine. Upon departure, unit was working.
Scheduled Maintenance Tuneuo done on a Carrier AC. System is running as expected for the summer season.
Arrived on site and customer stated the unit was not cooling. Cycled unit and found unit severely overcharged and internal kicking out, corrected charge and is at this time cooling properly,
Diagnostic performed on a 2004 Carrier Air Conditioner. Cleaned off the outdoor coil. System is an older unit and struggling with the heat outdoors. Estimate provided to replace system with a newer high efficiency system.
cleaned outdoor condensing coil, replaced capacitor
Replaced a condensate pump for a central air system. System is fully operational at this time.
Diagnostic of a 2018 Goodman AC unit, tenant stated unit was not blowing cool air, ended up replacing honeywell thermostat with wifi.