Pickerington Heating and Cooling returned for a furnace tune up. They called ahead, arrived on-time and performed the tune up as promised. A capacitor needed to be replaced.
Diagnostic Performed Installed New Thermostat Honeywell T1 On Carrier Gas Furnace To Keep Furnace Running At Highest Performance For The Winter Season
Furnace tune - up and safety check performed on a Trane furnace unit. Confirmed that the system is working within manufacturer specifications.
Diagnostic Performed Unplugged Flame Sensor On Carrier Gas Furnace To Keep Furnace Running Efficiently For The Winter Season
Diagnostics ran on 1999 Carrier cooling system.
Provided estimate on Carrier "Infinity Series" 19 SEER Variable-Speed 3 Ton Air Conditioner.
Estimate for a new carrier furnace and AC !
Working on TRANE air conditioner and furnace
60600 PHC - SMA (Scheduled Maintenance Agreement)
2018 Carrier 16Seer SMA customer checkout..
Scheduled Maintenance Agreement - Fall Tune-up/ safety checkout on a Gas 2018 Carrier furnace
Carrier furnace tune up
Goodman furnace and air conditioning tune up