Diagnostic Performed Cleaned Flame Sensor on Bryant Gas Furnace To Keep Furnace Running Efficiently For The Winter Season
Customer stated he heard motor making loud noise and furnace would not turn on. Found system turned off on open limit code. Pressure switch is freed up. Removed and cleaned trap. No water build up. Inducer also over amping. Nothing stuck in exhaust or intake pipes. Recommend replacing inducer motor and pressure switches. Tech would need to replace these parts in order to finish diagnosing the furnace.
Furnace Tune-up and Safety Checkout performed on a Carrier furnace unit. System is now functioning within manufacturers specifications.
Replaced gas valves.