Arrived on site. Customer states the system outside would hum but not turn on. Customer turned off disconnect outside . Thermostat still on, 3 degrees temp drop downstairs filter okay on system. Blower running well. Customer turned off disconnect to system. Found 240v to unit and 24v supplied correctly. Found capacitor to be at 0/40 and 0/5. No signs of rupture from electric, failed due to age. Replaced with customers permission and cycled unit on. System is back to life regularly. Compressor pulling 5.8amps (normal) fan pulling .55amps (normal) system is fully operational at this time.
Diagnostic service performed. Arrived on site customer stats on the hot days the lines out side freeze up. . cycled unit on from thermostat. Customer getting new filter. Blower on good. 10 degrees temp drop on system. Gauged up to system outback and found it operating at 32/154 with 54 degrees super heat. Super heat calculated and should be 15-18 degrees. Charged system up to these specs with R22. Pressures at 59/190 super heat at 14.6 degrees. System temp drop is 23 degrees. System is charged up again and ready for the rest of summer. Used 13 ounces
Humidifier install in grove city
Bryant furnace repair
Carrier furnace tune up