Air Conditioning Service - AC unit tripped breaker - Turn thermostat on to cooling, check compresser and capacitor - both good. Check all wiring. See wire connecting to contactor to the common on capacitor shows signs of being burnt. Run new wire from contactor to capacitor with two new spade connections. Unit is now operating properly and safely in accordance with Manufacturer's specifications.