Dispatched our refrigeration technician to a health center in Laguna Hills, California. One of their their three door freezers was icing up around the middle door. Upon inspection, our tech discovered that the wires for the door heater had come loose. He reconnected, and checked the remaining wiring was secure and no shorts had appeared. Unit online and at proper temp, icing issue resolved.
Dispatched our refrigeration technician to a health center in Laguna Hills, CA. A pin had fallen out of the hinge in one of their freezer doors. Our technician inspected the unit and attempted to locate the fallen pin, but was unable to find it. Employees did not have it. Per their recommendation, inspected several other freezer and found several with missing pins. Made temporary repairs to two freezers so that doors would close properly, and will order necessary pins for replacement.
Approved repairs were scheduled today for several freezers at our commercial customer in Laguna Hills, California. Five freezers had failed light bulbs that our technician removed and replaced. No other deficiencies found and all freezers operating normally now.
Dispatched our commercial refrigeration technician to a customer in Aliso Viejo CA for a freezer running hot. Their #6 True freezer was at 28 degrees. Troubleshooted the system and found that the evaporator coil had frozen over due to a bad defrost timer. Need to source and replace the timer, defrosted system and unit is running temporarily until full repairs can be made.