Approved repairs were scheduled today for several freezers at our commercial customer in Laguna Hills, California. Five freezers had failed light bulbs that our technician removed and replaced. No other deficiencies found and all freezers operating normally now.
Dispatched our commercial refrigeration technician to a customer in Aliso Viejo CA for a freezer running hot. Their #6 True freezer was at 28 degrees. Troubleshooted the system and found that the evaporator coil had frozen over due to a bad defrost timer. Need to source and replace the timer, defrosted system and unit is running temporarily until full repairs can be made.