Javier did a great job with the assessment and photos. We have a clear idea of how to proceed with repairs to eliminate the problem.
A management office for a mall was scheduled for PM service today in Anaheim, California. Their air conditioning equipment was inspected, following our standard 180 minor service schedule. All units were running well, and no items to report.
Out technician returned to a restaurant in Anaheim CA to work on one of their commercial freezers. The unit had been leaking on the previous visit, and our technician brought a new drain line heater to stop the drain line from freezing. The technician also repaired the drain line adapter that was leaking. Insulted the drain pipe and wired in the heater. Confirmed system is running correctly again and no longer leaking.
Dispatched our Anaheim CA refrigeration tech to a restaurant to inspect a walk-in cooler that was icing up. Upon arrival, our technician found the commercial cooler with a faulty door closer that will need to be replaced, to prevent air infiltration into the unit.
Our local Orange County AC technician returned to restaurant to replace a newly rebuilt blower assembly. After installing the new assembly, aligning all components and tightening pulleys and belts, the tech confirmed the system was up and running again with no more issues to report.
A customer in Anaheim CA reported that their AC unit was making a horrible noise. Sent our local technician to inspect the system, who found the condenser fan motor was failing and squealing. Unit is old and in overall poor condition, customer may consider full replacement over continued repairs.
A freezer manufacturer dispatched a request to replace a failed power cord for one of their customer's freezers. New cord was shipped to the site and our technician removed the existing cord and replaced with the new one. Tested for proper operations after repair, freezer back to freezing temperatures again.
Approved cooler repairs scheduled at a restaurant in Anaheim California. The customer's expo table needed to have the defrost timer replaced and rewired, and a new digital electronic thermostat installed. After making all approved repairs, our HVACR technician tested operations and confirmed the unit was operational again.
Dispatched our Anaheim CA refrigeration service tech to a restaurant, who reported their stand-up cooler doors needed repair. After inspecting the cooler, the tech determined that the doors could not be repaired. Steady use has exposed the insulation and there is no option for this door type to repair. Quoting two new doors for the site.
A restaurant in Anaheim California requested service. Their expo table had two fans that were frozen over solid with ice. Our technician troubleshooted the system, finding the suction pressure dropping. Noted that the line-set is incorrectly sized at the discharge line, and the defrost clock was set for 6 hours at night without any during the day, and that it was wired incorrectly to not shut down the compressor. Will need to source necessary parts and quote to repair.
Summer HVAC PM scheduled at a management office in Anaheim Hills CA. Site has one split system, which needed filters changed and both the air handler and condenser sections inspected. No issues found at this time, split system is working well and site comfortable.
Dispatched a repair technician to investigate a minisplit that had gone down. Found unit in poor condition, multiple leaks in the condenser coil. Do not recommend repairs as unsure they will hold. Will quote non-warrantied repair and a replacement option to customer.