Javier did a great job with the assessment and photos. We have a clear idea of how to proceed with repairs to eliminate the problem.
A health center in Anaheim Hills, California, reported that one of their critical AC units wasn't working. Our technician arrived and determined that he control board had shorted and the thermostat was damaged. Parts were available locally and our tech returned to the site same day to make repairs. And installing both parts, he tested the air conditioner. Unit cycled on and supply temperatures are back to 54 degrees. Space temp comfortable, job complete.
Phase two of an HVAC unit replacement scheduled today with a corrected curb at a restaurant in Anaheim, CA. Our installation team set the unit on its new curb, sealed all duct connections, ran new wiring, drain lines and gas lines. Added the new economizer and strapping. Powered up system and tested operations. Unit is online, job complete.
Spring HVAC maintenance performed at a management office in Anaheim, CA today. Our tech completed the standard major checklist items, including pressure testing and air filter change. Found a pitted contactor that will need to be replaced.
A management office for a mall was scheduled for PM service today in Anaheim, California. Their air conditioning equipment was inspected, following our standard 180 minor service schedule. All units were running well, and no items to report.
Out technician returned to a restaurant in Anaheim CA to work on one of their commercial freezers. The unit had been leaking on the previous visit, and our technician brought a new drain line heater to stop the drain line from freezing. The technician also repaired the drain line adapter that was leaking. Insulted the drain pipe and wired in the heater. Confirmed system is running correctly again and no longer leaking.
Dispatched our Anaheim CA refrigeration tech to a restaurant to inspect a walk-in cooler that was icing up. Upon arrival, our technician found the commercial cooler with a faulty door closer that will need to be replaced, to prevent air infiltration into the unit.
Our local Orange County AC technician returned to restaurant to replace a newly rebuilt blower assembly. After installing the new assembly, aligning all components and tightening pulleys and belts, the tech confirmed the system was up and running again with no more issues to report.
A customer in Anaheim CA reported that their AC unit was making a horrible noise. Sent our local technician to inspect the system, who found the condenser fan motor was failing and squealing. Unit is old and in overall poor condition, customer may consider full replacement over continued repairs.