Was very professional, explained everything, fixed the problem promptly. Even came on a federal holiday, could have come on a regular work day, but very much appreciated.
Response from RESSAC Climate Control:
Hi Sam, happy to hear that our technician was able to get your unit up and running again efficiently with the new control board. Thank you for the wonderful feedback!
Response from RESSAC Climate Control:
Thank you for the great review, Gabby. Glad to see that Franco could source parts locally and get you up and running today.
A customer in Beverly Hills, California, requested a visit to inspect their heater. Upon arrival, our technician inspected the south side AC, finding a clogged filter and removing it. Continued troubleshooting, and found the gas valve not opening. A short at the circuit-board and its harness was causing the valve not to open. We will quote a new board and harness. Heat is non-functional at this time.
Responded to a no heating call in Beverly Hills, California, site reporting that their thermostat was set high but space still too cold. Our A/C technician found that the t-stat was not reading the correct temperature, causing the unit to run when not needed. Replaced the faulty thermostat and tested the system. Space back down to acceptable temperatures per onsite staff, no more issues to report.
Dispatched our Beverly Hills CA air conditioning technician to a commercial property for Spring Maintenance. Arrived onsite and discovered the unit was disconnected and the roof currently being worked on in preparation for replacement. Spoke with manager on duty, will work with site and schedule for PM as soon as unit is available again.
A shoe store on North Rodeo Drive in Beverly Hills CA called in a no cooling report. Their commercial Carrier package AC was down due to its compressor not pumping. The belt and compressor contactor are in poor condition. Will quote necessary repairs to the customer, site is at 50% cooling capacity at this time.
Quoted HVAC repairs for a commercial customer in Beverly Hills were scheduled today. All units had their condenser coils cleaned, and two Carrier systems had condenser fan motors, blades and capacitors replaced. Tech also cleaned off economizer filters. Tested and cycled all repaired units before departure. Job complete, site comfortable.
Beverly Hills, CA: Commercial HVAC maintenance scheduled for a luxury goods store on North Rodeo Drive. Full cooling season PM, completed Spring checklist including testing pressures and testing for refrigerant leaks with electronic leak detector, inspecting electrical and replacing filters. Units functional and site cooling. Minor recommendations on two units, two fan motors overheating, will quote to customer. PM complete.
Dispatched our Beverly Hills CA air conditioning tech to inspect a commercial AC unit at an office building. The technician found that the heat had stopped working due to an overheating inducer motor. The run capacitor was failing. He was able to source the part from a local part house and return, replacing the capacitor and cycling the unit back on. Heating operational again, amperage good and no more issues at this time.
Our Beverly Hills AC technician returned to completed approved repairs on a commercial Carrier unit. The tech repaired a damaged drain line, running approximately 45 feet of PVC, and replaced a failed condenser fan motor and blade. Tested line drainage and cycled unit. Site operational again and unit cooling.
Dispatched our Beverly Hills, California, commercial HVAC tech to a customer reporting a no cooling issue. Upon arrival, our technician found their 5 ton Carrier air conditioner iced up. After defrosting the system, discovered the unit low on refrigerant with a small leak on the core valve. Replaced caps, pressures holding. Recharged unit with refrigerant. Also noted that the condenser fan motor is over-amping. Will recommend fan motor replacement to customer. Unit working at this time.
Spring preventative AC maintenance was scheduled for a clothing retailer in Beverly Hills, California. The technician serviced all 6 commercial Trane air conditioners, swapping out all filters, inspecting components and washing condenser coils. Confirmed units functional and ready for summer heat load.
Approved air conditioning repairs scheduled for a retailer in Beverly Hills, California. Their commercial 10 ton Trane package unit had a failed compressor contactor that had to be replaced. After making repairs, tech cycled and ran system to confirm all ops. No more issues to report, unit running normally now.
Major A/C PM scheduled for our commercial customer in Beverly Hills, California. Spring checklist completed, including condenser coil cleaning, amperage testing, filter replacement and cycling. Did find the #3 Trane air conditioner with a burnt compressor contactor that will need to be quoted. All other units operational.