A travel company in Burbank, California, requested AC service on their commercial air conditioners. The technician traced the problem to an ICP unit in the middle office that was low on refrigerant. Found access valves loose, tightened valves and recharged system. Performed leak search for any other leak sources, none found. Cycled and tested system. Site comfortable again.