Our Sacramento area HVAC controls returned to a business in Citrus Heights CA to complete installation of a new app for their system. Ran through system with EMS technician, completed installation and confirmed all systems operational.
A vitamin store in Citrus Heights CA reported a water leak from one of their reach-in coolers. Our commercial refrigeration tech found the cooler's drain line backing up, causing primary drain pan under coil to over-flow and not properly flow into secondary drain pan. Cleared all lines with nitrogen, cleaned out water from bottom shelf of cooler and cycled system. Unit draining normally now, job complete.
AC repair tech returned to complete approved work at a cell phone provider in Citrus Heights, California. The technician replaced the previously diagnosed burnt out blower motor and a run capacitor. Tested and confirmed operations normal. Site cooling and unit OK again.