Our controls technician returned to a commercial property in Citrus Heights, CA, to install a new supply sensor on their air conditioner. After making repairs, our technician called into the EMS support and confirmed all other systems were online and operating correctly. Job complete.
Energy Management controls installed today at this commercial property in Citrus Heights, CA. Phase 1 completed, VFDs installed on prepared equipment. Troubleshooted additional issues with EMS, confirmed RTU#1 will need a new sensor. Will source part and return.
Our Sacramento area HVAC controls returned to a business in Citrus Heights CA to complete installation of a new app for their system. Ran through system with EMS technician, completed installation and confirmed all systems operational.
A vitamin store in Citrus Heights CA reported a water leak from one of their reach-in coolers. Our commercial refrigeration tech found the cooler's drain line backing up, causing primary drain pan under coil to over-flow and not properly flow into secondary drain pan. Cleared all lines with nitrogen, cleaned out water from bottom shelf of cooler and cycled system. Unit draining normally now, job complete.
AC repair tech returned to complete approved work at a cell phone provider in Citrus Heights, California. The technician replaced the previously diagnosed burnt out blower motor and a run capacitor. Tested and confirmed operations normal. Site cooling and unit OK again.