Fall Maintenance Services completed for a loan shop's air conditioners in Compton, California. Site has two units, both were fully inspected and tested for heating operations. All filters replaced, belts changed and dated. No issues to report at this time.
Our Compton area commercial AC technician returned to a rental store to install a new circuit board and temperature sensors. He also finishing charging the system with 410 refrigerant. Tested and ran system, confirmed the Ruud unit was operational again. Changed batteries on the thermostat.
A rental store in Compton California was scheduled for approved air conditioning repairs today. The technicians were replacing a condenser coil and damaged reversing valve on a commercial Ruud unit, as the original coil had been stolen. After installing the new coil, re-piping to the drier and brazing all connections, the technicians recharged the system. While testing the system after recharging, they found that the defrost board and an outdoor air coil sensor were not functioning properly. Will order and return to complete work.