Technician Show concern in he's Job. Ask questions about the problem and communicate about he's performance.
A restaurant in Corona, CA, reported one of their ice machines was not working. Our refrigeration tech arrived and was told both ice machines were not working well. He inspected both Hoshizaki systems, finding one evaporator iced over and a second machine that was off due to constant beeping. Turned off 1B to let it thaw, and found 1A low on refrigerant. Performed basic leak search and was unable to find the leak. Will need to return and complete a full leak test and additional diagnose on both ice machines.
Approved repairs were completed today for a Omnitemp expo line unit in Corona California. The system needed new air diffusers installed to increase the airflow for the trays. After completing the repair and confirming no damage to the evaporator coil, the system tested operational. Job complete.
Completed full site survey of all air conditioning and refrigeration equipment for a commercial customer in Corona, California. All make, model and serial numbers have been recorded. Our Sales department will provide the customer with a quote for recurring maintenance.
A restauarant in Corona, California, reported that their ice machines were not working. Upon arrival our tech found the first Hoshizaki ice maker with a hole in the spout, preventing water from reaching the compartment to make ice. Tech was able to make a temporary repair while new spout is on order. The second ice machine he found the check valve was being bypassed by the water and dumping it straight to the drain. Removed and cleaned check valve, replaced and tested. Ice machine #2 up and running normally now.
Dispatched our Corona CA area technician to a restaurant for a second opinion on the state of their air conditioner. Our technician arrived onsite, checked in with management and proceeded to the roof. After obtaining all asset information the technician surveyed the systems. All units were in poor condition, no filters as they'd been removed and left on the roof. All condenser and evaporator coils were clogged. Units #1 and #3 are in the worst condition, rusted out and multiple failures. #2 and #4 have been repaired before. #4 was off due to a broken belt. Was able to get #4 up and running with a spare belt for now. Will quote all necessary work for the customer, including the replacements.
Our Corona California area technician responded to a no cooling call. Back air conditioning unit wasn't working. Upon arrival, found that the air filter for the system was badly clogged, allowing little airflow and causing the evaporator to ice over. System was slightly low on refrigerant, will recommend a leak search, unit is working for now.
Dispatched our Riverside County technician back to a vitamin store to complete approved HVAC repairs. Our tech replaced the blower motor and pulley on the #2 Carrier unit, and repaired melted wiring. Also found the unit had 3 blown fuses and burnt out contactor, that he was able to replace from truck stock. Continued troubleshooting the unit and found that the CLO board and thermostat had also failed. Will order parts ASAP to return and resolve.
Commercial HVAC repair. Diagnose and perform annual heating and air conditioning preventive maintenance on Lennox system. Inspect heat exchanger for deterioration, check refrigerant charge and fan switch. Clean and clear drain lines and pans. Replace air filters. Check for adequate air flow. Heating and cooling maintenance complete which will help extend the lifespan of equipment and improve overall unit performance.
Home goods store in Corona, CA, was due for routine HVAC maintenance. Technician inspected all components for cooling season, changed filters and belts, took photos and recorded issues with the #2 Lennox air conditioner. #2 had two pitted compressor contactors. Other units working well.