A cash loan store in Downey California reported their AC not working. Our technician inspected the space and found evidence of the system freezing up. Thermostat was set very low. Reset thermostat, confirmed all other operations.
A home goods store in Downey CA reported that their sales floor was too warm. The technician found two commercial HVAC units with issues: their #6 Lennox unit had a main board set to test mode, reset and adjusted settings to normal operations and system came back on as expected. Also found the #1 Lennox system with a bad condenser fan motor that will need to be quoted. Site cooling now, will quote additional repairs to customer.