A commercial customer in Indio, California, reported that their boiler pump was leaking water. Upon arrival our technician found the system's circulation pump leaking due to a shaft seal failure. Due to condition of pump, recommending replacement of entire part. Our tech shut off the isolation valves, locked out/tagged out and got all equipment data necessary to quote for repairs.
Approved air conditioning repairs were scheduled for our Indio CA customer today. Their AAON unit had two failed transformers that needed to be replaced. After wiring in the new transformers, our technician cycled the system and confirmed all other operations were normal. Job complete.