Dispatched our HVAC repair technician back to a business in Laguna Niguel CA for approved repairs on their exhaust fan. The restroom unit had a failed motor that needed replacement. After installing the new motor our technician tested operations. Exhaust fan working as expected now.
PM tech dispatched to a Laguna Niguel, CA, chiropractor's office to perform routine maintenance. Filters were changed on the single Carrier air conditioner, amps checked, no issues to report.