Approved freezer repairs were scheduled today at a health center in Long Beach, CA. Their Traulsen system needed a new evaporator cover and gasket. After making adjustments, our technician installed the new gasket and then the evaporator lid. Monitored system until temperatures returned to negative. No more issues to report.
A health clinic in Long Beach, California, reported one of their Traulsen freezer was leaking and icing over. Our local refrigeration technician inspected the unit, and found that the evaporator cover was damaged, and the top cover gaskets were worn, letting in air and causing unit to ice over and then melt. Will order parts, made adjustments to reduce icing for temporary operations.
Fall maintenance was scheduled today at a health food store for their air conditioners and their refrigeration equipment. All systems were inspected, air filters changed and site prepped for winter months. No issues to report.
Dispatched our Long Beach CA technicians back to a restaurant to complete installation of a new ice machine. Old unit was evacuated of refrigerant, disconnected and removed for disposal. Prepped space and set new unit, reconnecting all refrigerant lines and wiring. Resealed roof jack, cycled system to confirm ice was being made. New unit installation complete.
Dispatched our commercial refrigeration technicians to a Long Beach CA restaurant to install a new ice machine provided by the customer. Disconnected all power, refrigerant lines, water lines and drain lines. Removed old system and set new ice maker. Reconnected all connections. Leak tested all linesets after installing and resealed the roof jacks. Ran ice cycle, removed, cleaned, and ran again. New system online.
Dispatched our Long Beach CA refrigeration technician to inspect the dry storage freezer at a restaurant. After troubleshooting the system, the technician found the evaporator hissing, low on refrigerant. Need to perform a leak search and repair, replace the filter drier and assess. Signs of previous refrigerant repairs are visible.
A restaurant in Long Beach CA reported that their air conditioning in the host area was not working. The technician found the ICP system low on refrigerant. Also found a second unit with a bad capacitor which he was able to source the part for locally and replace same day. Will quote for additional repairs needed for the first A/C unit.
Quoted refrigeration repairs scheduled today at a restaurant in Orange County. The Continental refrigerator onsite needed new compressor start components.
A cell phone store in Long Beach, CA, requested repairs on a vent over their manager's office. Vent was found dangling slightly and site was concerned it would fall. Technician was able to disconnect and reconnect with new straps to secure vent. Site also has dirty vents and filters. Will return with filters and clean vents per customer approval.
AC technician arrived at a beauty salon store in Long Beach, CA. Employees reported that their thermostat was blank and site was warm. After troubleshooting, the tech found the package Carrier unit down with three blown fuses. Parts were sourced, fuses were replaced and HVAC returned to proper operations. Space cool again.
Washed coils on a/c unit. Found no other issues.