Dispatched our technician to a pharmacy in LA County that reported a cooler not operating. Upon arrival our refrigeration tech inspected the unit and found the breaker tripped. Unit had a badly clogged condenser coil that needed to be cleaned and blown out. After wiping down the cabinet area and testing all components, our tech reset the system. Open air cooler back online and operating at 39 degrees.