Dispatched our Marina California A/C technician to a loan shop where the heater had stopped working. The thermostat onsite was set to 96 degrees but the space was still measuring 70. On the roof, our tech found that the run capacitor had failed causing the blower motor to stop working. Replaced the capacitor. The motor is working again but may need to be replaced in the future. Heat operational.