Air conditioning maintenance performed at an office building in Marina del Ray, California, today. All heating components tested and confirmed safe, all filters changed and belts inspected. No issues to report at this time.
An office park in LA county reported two of their AC thermostats not working. The site had purchased two NEST t-stats and asked if we would install them in place of the faulty ones. After confirming both old thermostats were no longer holding their programming, our technician removed them and installed the new NEST stats, reviewing operations with the staff for future use.
An office building in Marina del Rey CA was scheduled for their major spring AC PM. Upon arrival, the technician inspected and tested all equipment, swapped out all filters, flushed drain lines and pans. 4 out of 5 units have deteriorating coils, and unit #4 has a condenser fan motor with noisy bearings and is leaking oil. Will quote necessary repairs to customer, will also recommend future replacement for the deteriorating units (salt air has rusted out much of the equipment). PM complete.
RESSAC tech arrived at an office building in Marina del Rey, California, to inspect their northwestern corner AC. Technician found that the package Carrier needs a new inducer fan motor assembly. Existing inducer motor bearings have failed, and the inducer wheel is rusted through causing the wheel to become unbalanced. Both issues were causing the AC to vibrate loudly. Unit turned off for safety now, will quote repairs.
Dispatched our Marina del Rey area HVAC technician to perform preventative maintenance on their a/c units. Technician replaced filters and inspected all electrical, coils, motors. Units are older but functional. Coils need to be washed. Will quote for chemical cleaning.
RESSAC tech serviced an office complex in Marina del Rey, California, for its annual heating air conditioning maintenance. Heating side equipment was inspected and tested, filters and belts were replaced. Heat exchanger in good condition. Systems working well.
Local office building was scheduled for their May AC preventative maintenance. The technician swapped out filters, blew out condenser drains and checked over all components. No issues to report, site in good condition.