A Merced, CA, customer requested emergency refrigeration service for their Turbo Air cooler that wasn't keeping proper temperature. Upon arrival our technician found the unit running and reading 32, expected temp. Tested main controller, thermostat and tested again RESSAC supplied thermometer. All temps accurate, verified no apparent leak issues or electrical failures. Advised MOD to contact EMS to confirm their readings are accurate versus actual temperature onsite. Job complete.
Retrieved permit for upcoming HVAC installation work in Merced, California today. Our Install technician also coordinated with onsite management to prepare for the work. Noted that wasps have moved into the hold unit, will advise return crew to bring wasp spray.
HVAC survey completed for planned air conditioning replacement at a commercial building in Merced California. All platform measurements taken, roof layout and crane access noted. Will report back to main office and quote replacement for customer.
Dispatched our HVAC repair tech to a commercial property in Merced California for approved work. Our technician replaced the zone sensor and wiring for RTU1. Adjust T-stat settings for zone sensor application. Checked system operation, discharge temp 56°F. Thermostat reading 76°F a delta of 20°F. Zone sensor, T-stat, and RTU unit is in working condition.
Dispatched our Merced California area HVAC technician to a commercial customer for approved work. Upon arrival, after checking in with the IVR, mall management and store manager, our technician proceeded to the roof to replace the disconnect on a commercial Carrier system. Spliced and replaced damaged wiring, wired in disconnected. Powered up the unit and tested. System providing a 30* split despite high heat-load in store. Job complete.
Our Merced CA HVAC technician responded to an urgent call from a commercial customer, reporting a water leak in their space. Upon arrival, our technician found the AC unit very dirty, with clogged filters, overflowing condensate pan due to built up sediment, and compacted refrigerant coils. Our technician proceeded to clean the entire system, changing all filters, chemically washing coils, clearing and cleaning pan and drain line. System working well at this time, water leak resolved.
Dispatched our Merced, California, technician to a clothing shop to perform approved work. Their commercial Carrier air conditioner had a failed compressor. The tech removed the old compressor, recovered refrigerant. Replaced compressor, filter and liquid driers. Verified no leaks remaining in system. Recharged. Tested and confirmed unit back up and operational.
Refrigeration technician dispatched to jobs in Merced, CA. First call was for Walgreens with walk-in freezer running warm. After free inspection technician found leaking compressor valve plates. Presented quote to customer for retrofit of new valve plates on compressor.