Very nice guy and friendly!!
HVAC preventative maintenance scheduled at a commercial property in Mission Viejo, CA today. Services completed per the PM agreement scope, and a few issues found while onsite. All units need an additional coil cleaning this year, unit #6 needs a new A2 sensor and #9 needs the economizer screen replaced.
A scheduled air conditioning maintenance was completed today at an imports store in Mission Viejo, CA. All PM services were performed per the customer's scope, including exhaust fan return grills. No deficiencies found, PM complete.
A chiropractor's office in Mission Viejo CA was scheduled for HVAC maintenance today. Standard summer, minor service: all filters changed, units inspected and deficiencies noted. System is functional, but has a rusted capacitor that needs to be replaced and a drain line that has cracked. Will quote repairs for customer.
San Diego county tech arrived at a home goods store to perform their spring maintenance. Replaced filters and belts, checked amps and exhaust fans. Units in good working shape.
Refrigeration tech returned to a weight loss center in Mission Viejo, CA, to perform approved work. Traulsen freezer #3 was in need of a new capacitor. Tech was able to source and replace. Freezer back to normal operating temperatures, will need to quote failing gaskets but that's not affecting performance at this time.
Orange county maintenance tech arrived at a medical office to perform the Spring maintenance. Filters were changed, amps checked and system tested. Unit running well.