Approved HVAC repairs scheduled for a loan store in Palmdale California. The technician had to replace a faulty condenser fan motor, blade, capacitor, and compressor contactor. After installing new parts, the technician tested the unit and monitored to bring space back to comfortable temperatures. No more issues to report.
Dispatched our Palmdale California commercial HVAC technician to perform spring maintenance at a loan office. After completing the spring checklist, checking all ops, pressures, coils, the technician found a noisy condenser motor for for unit #2. Motor is starting to fail, will recommend change-out of motor along with blade and one contactor. No other issues to report, PM complete.
Our Palmdale, CA, area technician performed AC Maintenance for a retail clothing store. Completed standard scope including filter change, coil washing and cooling start-up. Also called in to EMS Monitoring service to check for active HVAC alarms. Inspected on alert on RTU #1's damper. Damper activating normally upon testing, error on monitoring side. EMS will investigate. All other equipment working fine.
Dispatched our commercial HVACR tech to perform standard maintenance at weight loss center in Palmdale, California. Technician serviced air conditioners and freezers onsite, changing filters and testing systems in prep for spring/summer. No issues to report, all equipment working well today.
Los Angeles county AC tech arrived at a finance office to perform approved work. The technician replaced capacitors and belts on both Carrier air conditioners. Tested and ran units after making repairs. Equipment working well, temperatures comfortable inside space.
RESSAC maintenance tech dispatched to Palmdale, CA, to perform standard fall maintenance at a financial aid office. Changed filters, checked belts, tested and confirmed all components were operating normally. Noted two cracked belts and failing capacitors for both motors. Recorded issues to report to the customer, units running fine despite deficiencies.
Los Angeles county a/c technician dispatched to complete approved repairs at a home goods store. Both units needed compressor contactors replaced, and the tech repaired an electrical short on unit #3. Tested system, confirmed operations had returned to normal and site cooling well.
Commercial HVAC technician returned to a Palmdale, CA, mobile provider store to complete approved work. The technician checked in with the manager and went up to the roof, replacing the failed condenser fan motor on the 2nd Carrier air conditioner. Tested system, confirmed operations normal and site cool.
RESSAC tech arrived at a lending office in Palmdale, CA, to complete approved repairs. Tech brought a new condenser fan motor, blade and capacitor for their 5 ton Carrier unit, and replaced needed parts. Unit is back at a 56 degree supply and space comfortable.
A finance office in Palmdale, California, was on schedule for recurring ac filter change and standard maintenance. After filter swap, technician inspected both package units and found them working well. No deficiencies to report.
Approved repairs scheduled at a apparel and accessories retailer in Palmdale, CA. Their Trane air conditioner needed properly sized filters, a new belt and a coil cleaning. After completing quoted work, the tech tested and cycled the equipment. Units running well now, no issues to report.
Summer AC maintenance and quoted coil cleaning on schedule today at this cash loan store in Palmdale, California. Power washed and chemically cleaned all unit coils, changed filters and inspected. Unit #1 has a pitted contactor. Will quote to customer, not affecting cooling at this time but may fail during times of greater heat load.
Time for recurring maintenance at a jewelry store in Palmdale, California. Our technician inspected both Carrier air conditioners, changed filters and found no complaints or problems. Site comfortable today.
Los Angeles county AC maintenance tech dispatched to a mobile provider store. Performed their standard spring HVAC maintenance, changing belts and washing coils but no filter change per customer request. No issues found on the two Carrier units, PM complete.
An HVAC survey was requested at a Palmdale, CA, money lender. The AC technician inspected all equipment onsite, finding two Carrier package units. Equipment was 15+ years old, in fair condition but operational. Coils in poor shape. Noted all data-plates and uploaded for main office to quote preventative maintenance services per customer request.