Approved HVAC repairs were scheduled for a commercial customer in Porterville California. Their York air conditioner needed a new condenser fan motor and filters, a coil wash, and also had a refrigerant leak that needed to be located and repaired. After replacing the fan motor and filters and washing the coils, the tech was able to locate the leak on the service core valves and repair it. Replaced a worn belt as well while onsite. Job complete and unit running normally again.
A cell phone provider in Porterville California requested urgent service for an AC issue, store was at 82 degrees. Upon arrival, our technician found a bad run capacitor and condenser fan motor with worn bearings. Replaced the capacitor to get the unit running, will need to replace the fan motor. Also found the blower motor missing a support bracket, causing excess vibration and belt wear. Unable to locate missing nut inside unit, will source for repairs and bring a new belt. Air filters are badly plugged and coils are very dirty. Stage-2 possibly low on charge, and minor leaks found on the discharge service ports. Will quote all necessary repairs and return, unit running for now.
RESSAC commercial technician arrived at drug store in Porterville, CA, to perform quoted work on the walk-in cooler. The tech powered down the system, removed the original faulty defrost time clock and replaced it. Tested and verified unit operations, refrigeration equipment back to optimum temperatures and operations. Rite aid #5799 porterville came to out to change defrost clock for dairy cooler. Unit is on and fully operational at this time