A compressor replacement was scheduled today for a drink cooler in Redding California. The systems filter drier and service ports also needed to be swapped out. After recharging the system and monitoring the unit, the technician confirmed it is operational again.
A home good store in Redding, California, reported one of their HVAC units not cooling. Our AC technician found the Lennox unit tripped on high pressure. He traced the issue back to a failed relay for the condenser fan motor. Sourced a new relay locally and replaced it. Cycled system to test, unit is cooling sufficiently with a 20 degree split.
Redding, California, a/c technician dispatched to a home goods store for approved repairs. The Lennox AC needed the condenser fan motor replaced. Tech also replaced the capacitor and fan blade. Tested system, back up and running and site comfortable.
RESSAC HVAC technician arrived at warehouse to repair a Carrier package unit. Technician arrived at the location and got on the roof to inspect the unit. Unit was found to be low on refrigerant and the tech recovered the old refrigerant and replaced the liquid line drier. He then recharged the system and restored it to proper operation.