A home good store in Redding, California, reported one of their HVAC units not cooling. Our AC technician found the Lennox unit tripped on high pressure. He traced the issue back to a failed relay for the condenser fan motor. Sourced a new relay locally and replaced it. Cycled system to test, unit is cooling sufficiently with a 20 degree split.