Approved refrigeration repairs were scheduled today at a restaurant in San Bernardino, CA. Our technician had brought two new float swithes and four new distributor tubes
Dispatched our San Bernardino CA area refrigeration technician to a restaurant to inspect their cook line unit. The system was iced up and fans were not running. Our tech diagnosed a several faulty fan motors, and the evaporator coils were badly clogged. Quoting all necessary repairs to the customer ASAP.
A restaurant in San Bernardino CA reported that their walk-in cooler wasn't working. Dispatched our local commercial refrigeration technician who determined that the coils on their evaporator and condenser were clogged. Cleaned the coils thoroughly and pressures returned to normal. Noted that their defrost was was not timed correctly, their timer not keeping proper program. Will order and install a new timer.
A clothing retailer in San Bernardino CA reported that the fire alarm company had powered down three of their air conditioners, and wanted RESSAC to diagnose what had happened. Upon arrival, determined that the alarm company had been onsite for maintenance only, so our tech proceed to investigate, troubleshooting with EMS technician over the phone and cycling units. Was able to bring units #2 and #1 back online. #4 was not responding to control calls for cooling, will need to return with a new CAT-5 wire and resolve. Confirmed issues with management before departing.