Did a complete review of HVAC systems, friendly & professional.
Response from RESSAC Climate Control:
Hi Paul, we appreciate the positive feedback from Chuy's visit, thank you for the review!
I never see the bill so I can't answer question 2
Response from RESSAC Climate Control:
Thank you for the 5-star service review Ken! We appreciate the feedback, if you ever have any questions about our visits feel free to call into our office. Any of our Customer Service staff will be happy to assist.
New HVAC installation scheduled today at a commercial property in San Jose California. Two package units replaced, all piping reconnected, electrical rewired and operations tested. System operational and online.
Completed a pre-scheduled HVAC site survey for energy management controls in San Jose, California. Obtained all equipment data, electrical information and measurements required to complete upcoming project.
Dispatched our Northern California controls technician to complete comprehensive survey of a commercial site for upcoming installation. All equipment data acquired, measurements and notes for project taken. Site visit complete.
A cash loan store in San Jose California was scheduled for air conditioning repairs today. Their commercial York unit was down with a grounded compressor. Unit was completely out of refrigerant. Our tech sweated out the old compressor, installed the new one and pressure tested. Confirmed no leaks, recharged unit with correct amount of refrigerant. Restarted system and tested. Unit is cooling well now, no other issues at this time.
An air conditioning unit replacement was scheduled today at a vitamin store in San Jose California. The original unit was old when its compressor grounded, so the customer opted for replacement instead. The technicians met with the crane, had the old HVAC removed after disconnecting it and the new unit placed. Connected supply and returns, installed new drain lines and disconnect, secured system, replaced electrical. Ran and tested new unit, system is operational and site cooling again.
A car dealership in San Jose CA had a showroom with a bad exhaust fan motor. Our technician returned to replace the fan motor, disconnecting the system and removing the old parts, replacing with the new motor and then testing the exhaust. Exhaust fan is operational now and space comfortable. Checked out with manager on duty.
Commercial Energy Management System job walk in San Jose, California. Inspected all equipment for 3 buildings, confirmed AC unit data, inspected the existing control system located in the boiler room. Mapped out site for upcoming installation. Follow-up visit to be scheduled once EMS equipment is delivered.
AC service technician arrived for a survey at a cell phone store in San Clara county. Customer requested a thorough inspection of the heating components. Tech checked all heating items, no issues with the heat exchanger, gas valves and line were fine. Burners and gas pilots also OK. Unit not in need of replacement.
RESSAC AC technicians were dispatched to an auto dealership in San Jose, CA. Service department was no longer cooling. Three ICP HVAC units were down. RTU #4 had the programming set incorrectly on the thermostat. Unit #3 was not receiving line voltage, breakers operating but only intermittently. Breaker was reset and customer notified to request an electrician to address the breaker panel. RTU #2 was also down with a failed control board, which was quoted for the customer to approve. Area returned to partial cooling, awaiting customer approval for remaining repairs.
Commercial A/C tech arrived at retail store in San Jose, California to replace a condenser fan motor. He put the new motor in and tested all voltage to contactors. All components were found working.
RESSAC HVAC technician arrived at insurance firm to inspect and repair a downed AC unit. Tech found that the unit was not receiving any gas from the building and notified the manager to have the property owner have their gas turned on.