Did a complete review of HVAC systems, friendly & professional.
Response from RESSAC Climate Control:
Hi Paul, we appreciate the positive feedback from Chuy's visit, thank you for the review!
I never see the bill so I can't answer question 2
Response from RESSAC Climate Control:
Thank you for the 5-star service review Ken! We appreciate the feedback, if you ever have any questions about our visits feel free to call into our office. Any of our Customer Service staff will be happy to assist.
Our commercial controls technician was dispatched to a restaurant to investigate reported communication issues. Upon arrival, our technician tested the phasing switch on the controls and made adjustments. Reset parameters and checked in with EMS to confirm communication was back online and no more issues found.
Approved refrigeration repairs were scheduled today at a restaurant in San Jose, California. Their sandwich station needed new compressor start components installed. After wiring in new parts, our technician tested the system and confirmed all other components were functional. System back online and cooling per code.
Returned to a San Jose CA diner to confirm status of the sandwich counter's compressor. Our refrigeration technician re-examined the unit, and the compressor may not need replacement but we will not be able to determine 100% until the start components are replaced.
A diner in San Jose, California, requested service for both their air conditioner and a sandwich station. Our local technician confirmed the A/C was working well, but needed its thermostat reprogrammed. Moved on to the sandwich table and found it running at 59 degrees, low on refrigerant. The second box was at 87 degrees, with it's compressor pulling a vacuum on the low side and empty of refrigerant. The compressor had been replaced recently by another contractor. Will need to perform a full leak search and repair on both boxes, as well as install new liquid line driers.
New HVAC installation scheduled today at a commercial property in San Jose California. Two package units replaced, all piping reconnected, electrical rewired and operations tested. System operational and online.
Completed a pre-scheduled HVAC site survey for energy management controls in San Jose, California. Obtained all equipment data, electrical information and measurements required to complete upcoming project.
Dispatched our Northern California controls technician to complete comprehensive survey of a commercial site for upcoming installation. All equipment data acquired, measurements and notes for project taken. Site visit complete.
A cash loan store in San Jose California was scheduled for air conditioning repairs today. Their commercial York unit was down with a grounded compressor. Unit was completely out of refrigerant. Our tech sweated out the old compressor, installed the new one and pressure tested. Confirmed no leaks, recharged unit with correct amount of refrigerant. Restarted system and tested. Unit is cooling well now, no other issues at this time.
An air conditioning unit replacement was scheduled today at a vitamin store in San Jose California. The original unit was old when its compressor grounded, so the customer opted for replacement instead. The technicians met with the crane, had the old HVAC removed after disconnecting it and the new unit placed. Connected supply and returns, installed new drain lines and disconnect, secured system, replaced electrical. Ran and tested new unit, system is operational and site cooling again.
A car dealership in San Jose CA had a showroom with a bad exhaust fan motor. Our technician returned to replace the fan motor, disconnecting the system and removing the old parts, replacing with the new motor and then testing the exhaust. Exhaust fan is operational now and space comfortable. Checked out with manager on duty.
Commercial Energy Management System job walk in San Jose, California. Inspected all equipment for 3 buildings, confirmed AC unit data, inspected the existing control system located in the boiler room. Mapped out site for upcoming installation. Follow-up visit to be scheduled once EMS equipment is delivered.
AC service technician arrived for a survey at a cell phone store in San Clara county. Customer requested a thorough inspection of the heating components. Tech checked all heating items, no issues with the heat exchanger, gas valves and line were fine. Burners and gas pilots also OK. Unit not in need of replacement.