Response from RESSAC Climate Control:
Thank you for reviewing Kevin's visit, Kristen. Our technicians greatly appreciate the feedback! We will have a proposal for preventative HVAC maintenance prepared for you with the equipment data Kevin obtained.
Received a service request for thermostat at a bank in Santa Barbara, California. Our commercial technician inspected the conference room unit, finding the system operational but the thermostat blank. Traced a short in the low voltage wiring. Replaced the wiring and reset the thermostat programming. Job complete.
A loan office in Santa Barbar, CA, was scheduled for A/C maintenance today. We perform PM services for their server room only per their direction. All components inspected, pressures and amperages tested. No issues to report.
Dispatched our commercial AC technician to a Santa Barbara, CA, school campus for their winter maintenance service. The site has multiple air conditioners, split and package, spread across several roof levels. After visually inspecting all units, our technician found RTU#5 with a condenser fan motor running a high amperages. Recommend replacing it before the summer heat load causes unexpected failure.
A finance office in Santa Barbara, California, was scheduled for their routine minor HVAC maintenance today. We service one Leibert split system for their server room. Filter was removed and replaced, components inspected per minor service checklist. No issues to report, unit is running normally.
Winter Air conditioning maintenance scheduled today at a bank in Santa Barbara, California. All commercial units were inspected for deficiencies and filters replaced. Our technician found the #2 Day & Night system with an over-amping fan motor that should be replaced before it fails. Will quote recommended repairs to the customer. PM complete.
RESSAC returned to a retailer in Santa Barbara, California, to complete repairs on a York air conditioner. Our commercial technicians removed a failed blower assembly, replaced defective components and reassembled. System running well now, no more issues to report.
A commercial customer in Santa Barbara California was scheduled for air conditioning repairs today. Their #1 York system had a refrigerant leak on circuit #1. After performing the leak search and pressurizing the system, our technician found multiple leaks on both condenser coils, for both stages. The tech disconnected the circuits, leaving the system on fan-only operations, to protect the compressor. Will recommend coil replacement to customer, repair attempt not recommended.
Multiple HVAC repairs scheduled for our commercial customer in Santa Barbara, CA. One Carrier air conditioner required its condenser fan motor, blade and capacitor be replaced. A second unit had a pitted contactor and bad capacitor, and a third AC also had a pitted contactor. The technician completed all necessary repairs and tested the equipment afterwards, confirming all 3 units were functional again.
Our RESSAC technician arrived at a school in Santa Barbara, California, to survey all the commercial air conditioning equipment on site. Met with customer to discuss site needs, then inspected entire property. Gathered unit data for all air handlers, condensers and package units. Uploaded all asset information into service trade including air filter list. Visually inspected all units and found AHU #4 with a defective blower motor. Marked issue as a deficiency to quote. Survey is completed, will provide maintenance proposal for customer.
A specialty import goods retailer in Santa Barbara, California, to repair several units after finding issues on the last maintenance. Three York air conditioners needed new capacitors. Systems were repaired and tested, all functioning normally now.
Can't get the smoke smell out of your commercial building after the recent fires Santa Barbara? We offer comprehensive preventative maintenance and cleaning of air conditioning systems. We can also inspect your duct-work and advise whether you need duct cleaning. Other fire remediation solutions include electronic air cleaners and carbon impregnated filters. Call us for a consultation.