Dispatched our Santa Clara area AC tech to a restaurant to inspect a sensor issue. The technician inspected the #1 zone sensor as well as the thermostat which was blank. Troubleshoot with EMS, confirmed replacement of the sensor was needed. After replacing sensor continued troubleshooting, finding the economizer module had failed. Bypassed module to provide side with cooling. Will quote to return and replace module.