Dispatched our HVACR maintenance technician to a health center in Simi Valley, California. All equipment, air conditioners and freezers, was inspected for their spring service, all major checklist items per agreement completed. All units operational and maintenance finished.
Our local Simi Valley CA area technician responded to a freezer call at a health center. One of the freezer doors was popping open whenever the other was shut. After inspecting the True unit, our technician made adjustments to the gasket venting to allow the door to close properly. He also moved the top door pins back to allow the door to shut with more force. Other door no longer pops open, issue resolved.
Approved refrigeration repairs were scheduled today for a commercial freezer in Simi Valley, CA. The Traulsen freezer needed a new door, which our technician replaced. All systems functional upon completion, no more issues to report.
Our Simi Valley, CA, commercial HVAC tech arrived at an imports store to perform preventative maintenance on all their commercial AC units. He replaced all air filters, inspected electrical, coils, motors, and tested unit operations. Cleaned condenser coils and checked cooling supply temp, confirming all except #4 at 55 degrees. RTU #4 has two defective condenser fan motors and fan relays that will need to be replaced. Uploaded findings to job deficiencies. Confirmed all other unit operations with EMS and completed all maintenance paperwork per scope. Job complete.
HVAC Preventative Maintenance scheduled at a cash advance store in Simi Valley, California. Filters were swapped out, remaining components checked and confirmed operational. PM complete.
A Simi Valley, California, mobile provider had approved AC repairs scheduled today. Technician arrived and performed a leak search on the York air conditioner. Found the leak on the evaporator coil, fixed, pressurized system and recharged. Also cleaned coils on both units. Equipment back up and in running order.
Came out to clean all condenser coils on all freezers . All units working good
Maintenance technician arrived at retail store in Simi Valley, California to perform maintenance on eight Lennox package units. Tech checked and tested all units for defective parts. He replaced the filters and belts, reconnected all economizers, and noted that all units needed coil cleaning. All units were otherwise restored to proper operation and the manager was made aware that the coils would need to be cleaned.
Refrigeration technician dispatched to jobs in Simi Valley. First call was for weight-loss center with Traulsen 2 door reach-in freezer running hot and with blank thermostat. After initial inspection tech found defective control relay module. He replaced module and returned freezer to proper operation.