Response from RESSAC Climate Control:
Hi Donovan, thank you so much for the 5-star review for Barry's service earlier this month. We're glad that the noise problem in the stockroom was a quick fix with a new fan motor, and is no longer an issue!
Dispatched our maintenance technician to Stockton, CA, to service AC units and freezers for minor service. Both air conditioners are working well, no issues found on inspection, filters have been replaced. All freezers are operating at industry standard temperatures and draining well. PM complete.
Our HVAC controls technician servicing the Stockton, California area returned to a restaurant today to complete the installation of their new EMS system. After finalizing installation, our technician completed all paperwork and quality checks. Upon completing checklist, determined that there was a device malfunction that would need to be troubleshooted.
Day #2 of HVAC controls installation at a restaurant in Stockton, California. Finalized all wiring checks, confirmed programming and started commissioning with supplier.
Received an alert from a customer in Stockton CA, that one of their A/C units was showing an alarm. Our commercial HVAC tech found that system #3 had a belt that had jumped off the pulley. Confirmed the belt was still in good condition, re-adjusted the sheave and pulley and reinstalled. Unit back in working condition. Unable to check out with monitoring contact, no response so left a VM.
On arrival, checked out n with store manager. Found medium temp walk-in temp gauge reading 41-42degs. Used digital thermometers all reading around 37-39degs. System is fully operational. Obtained signature on work acknowledgment.
On arrival, call Richard and left message notify him I was on site. Checked in with manager. Checked in with mall security. Found medium temp walk-in temp about 60degs inside. Gained roof access. Found condensing unit not running. Found relatable high pressure switch was tripped. Reset switch and condensing unit immediately came on. Pressures were reading normal. Found evap coil with a lot of build of debris. Cleaned evap coil. Condensing fan motor amps are 0.38. Condensing fan motor capacitor is 4/4uf. Compressor amps are 5.45. Finding nothing out of the ordinary. Will come back tomorrow to follow up. Obtained signature on work acknowledgment.
A jewelry store in Stockton California reported that their AC unit had gone down. Our technician arrived and first checked the breaker panel, confirming here was power to the unit. Found system not running due to a 24v short at the Y circuit, where a wire nut had fallen off and grounded causing 3amp fuse to blow. Our tech replaced the wire nut with newer one and replaced blown fuse. System cycled on in cooling with a 23deg split. Unit is now operational.